Quelfire Seal Bags
€6.23 – €12.61
QFP QuelStop Intumescent Fire Pillows help prevent the spread of fire through metal cable trunking systems that penetrate through fire compartment walls.
Features & Benefits
- Fire Tested to BS EN1366-3-2009
- To reinstate fire resistance through walls
- Easy to install and remove
- Available in 3 different sizes
- Remains flexible between -20C to +130C
- Moisture resistant lining
- Trunking areas of use: directly through flexible walls & directly through rigid walls
- Product Specifications
Quelfire Intumescent Fire Pillows can be used inside steel cable trunking up to 150x150mm where they penetrate fire compartment walls.
They are available in 3 different sizes allowing flexibility in choice to ensure that the trunking is fully sealed even with varying number of cables in them. The cables should not take up more than 60% of the available space inside the trunking and the Pillows should then be installed lengthways, centrally positioned within the wall, filling the remaining space.
Typical Installation Detail Directly through walls
Ensure the supporting construction, aperture, services and site conditions are within the tested scope of application.
Apertures in the wall should be cut as close as possible to the size of the steel trunking ? ideally with a maximum 10mm annulus but in any case not exceeding the maximum sizes given below:
|Penetration Service||Aperture in wall|
|Steel Trunking |
up to 50 x 50mm
|Up to 70 x 70mm|
|Steel Trunking |
up to 150 x 150mm
|Up to 170 x 170mm|
Ensure the inside of the trunking and cables is clean and clear of loose dust particles.
Install the QuelStop Intumescent Fire Pillows lengthways within the trunking and in such a way that all joints are staggered in each layer and all gaps within the steel trunking system are filled in a manner that ensures a tight compression fit. They should be finally positioned so that they are centrally positioned within the fire compartment wall.
Fill the void around the trunking, using an appropriate backing material such as PE backing rod, glass wool, stone wool or ceramic wool and then apply QuelStop Intumescent Acrylic Sealant to a minimum depth of 10mm.
|Size (mm)|| |
50×50, 50×185, 385